3701-31-04 (B)(1)(a) / Outlet covers shall be installed/secured/in compliance
Critical The skimmer equalizer lines are not VGB compliant.
COVER THE EQUALIZER LINES WITH VGB COMPLIANT COVERS OR PLUG THE OUTLET AT THE POOL WALL. Correct By: 30-Jun-2018
3701-31-04 (B)(6)(t) / Equipment/chemical/storage areas are free of hazards/accessible only to authorized personnel.
Critical The filter room with chemicals was not locked.
KEEP THE FILTER ROOM LOCKED. Correct By: 21-Jun-2018
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request. KEEP AN OFFICIAL WEEKLY RECORD LOG TO RECORD FREE, TOTAL, AND COMBINE CHLORINE, pH, AND ALKALINITY. KEEP THE LOG AT THE POOL. Correct By: 30-Jun-2018
3701-31-04 (B)(6) / Equipment is maintained per manufacturers specifications.
Equipment was not maintained per manufacturers specifications. The skimmers are missing the weirs.
All equipment must be maintained in accordance with the manufacturers specifications. REPLACE THE MISSING WEIRS IN THE SKIMMERS. Correct By: 30-Jun-2018
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 20-June-2018