3701-31-04 (B)(1)(a) / Outlet covers shall be installed/secured/in compliance
Critical Outlet covers were not secured. Screw missing.
Do not operate the pool when the outlet covers are not secured. Secure the covers prior to the pool being placed back into operation. INSTALL MISSING SCREW IN DRAIN COVER. REPLACE FRAME IS NECESSARY.
3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical Chlorine disinfectant residual was less than 2 ppm for the spa
Do not operate the pool when the disinfectant residuals are less than what is required. Ensure the chlorine disinfectant residual is at 2 ppm or above prior to placing the spa back into operation. THIS IS A CRITICAL OPERATIONAL ITEM AND POSES AN IMMINENT HEALTH HAZARD. CLOSE SPA UNTIL CORRECTED. CALL ME WHEN CORRECTED. OPERATOR WAS NOTIFIED BY PHONE VOICE MAIL TO CLOSE SPA. OPERATOR CALLED BACK AND AGREED TO CLOSE SPA. Correct By: 22-Apr-2022
3701-31-04 (B)(1)(e) / Automatic Chemical Controller (ACC) shall function properly.
Critical Automatic Chemical Controller (ACC) was not functioning properly at the time of the inspection
Do not operate the pool when the ACC unit is not functioning properly. Ensure that the ACC unit is functioning properly prior to placing the pool back into operation. CLOSE SPA UNTIL CORRECTED. Correct By: 22-Apr-2022
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request. KEEP RECORDS.
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Total alkalinity was less than 60 ppm.
Raise the total alkalinity to at least 60 ppm. ADJUST ALKALINITY Correct By: 25-Apr-2022
3701-31-04 (C)(8) / Spa water is drained at least every 30 days and is recorded
Spa water was not drained in the last 30 days.
Drain spa immediately and clean before placing the spa back in operation. COMPLETELY DRAIN SPA EVERY 30 DAYS.
Facility Type: Spa
[?] Inspection Type: Follow-up
Inspection Date: 26-April-2022
|Manager indicated that the spa is still not open. Pool maintenance has been contacted for repairs.|