3701-31-04 (B)(6)(c) / Cross connection hazards shall be prevented.
Repeat Cross connection hazards were present
Remove all cross connection hazards from the pool area. PROVIDE AN AIR GAP ON THE FILL SPOUT. Correct By: 17-Jun-2019
3701-31-04 (B)(6)(f) / Required turnover rates are sufficient
Required turnover rates were not met.
Have the circulation system evaluated to determine why the turnover rates are not able to be met. INCREASE THE FLOW RATE TO AT LEAST 13 GPM. Correct By: 17-Jun-2019
Facility Type: Special Use
[?] Inspection Type: Standard
Inspection Date: 12-June-2019
|Our records show: The main drain suction outlet cover (AquaStar 1216) was installed 8/11/2014. The cover has a 5 year life span and must be replaced before 8/11/2019.|