3701-31-04 (B)(1)(a) / Outlet covers shall be installed/secured/in compliance
Critical Several of the skimmer equalizer outlets are not covered with a VGB compliant cover or plugged.
COVER THE SKIMMER EQUALIZER OUTLET WITH A VGB COMPLIANT COVER OR PLUG THE OUTLET AT THE POOL WALL. Correct By: 27-Jun-2019
3701-31-04 (B)(6)(y) / Chemicals are properly stored/used
Critical Chemical containers were stored without labels identifying the contents.
Label and properly store all chemical containers to avoid a chemical reaction or unnecessary exposure. LABEL THE CHLORINE TANK Correct By: 09-Jul-2019
3701-31-04 (B)(6)(c) / Cross connection hazards shall be prevented.
Cross connection hazards were present. The hose bib in the pump room was not back flow protected.
Remove all cross connection hazards from the pool area. PLACE A BACKFLOW PREVENTER (ASSE 1011) ON THE HOSE BIB LOCATED IN THE PUMP ROOM. Correct By: 09-Jul-2019
3701-31-04 (B)(6)(s) / Perimeter barrier is in good repair to prevent unauthorized entry
The fence has gaps of more than 4 inches between the bottom of the fence and the ground in 2-3 locations.
CLOSE THE GAPS BETWEEN THE BOTTOM OF THE FENCE AND THE GROUND SO THAT THERE IS LESS THAN A 4 INCH GAP. MOUNTING UP MULCH OR GRAVEL UNDER THE FENCE WOULD BE ACCEPTABLE. Correct By: 09-Jul-2019
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 25-June-2019
|Our records show: The main drain suction outlet cover (Waterway 640-472xV) was installed 5/18/2015. The cover has a 7 year life span and must be replaced before 5/1/2022.|
-Post a "DANGER: POOL CLOSED" sign on the gate at the end of the season and at the end of the day.