3701-31-04 (B)(1)(a) / Outlet covers shall be installed/secured/in compliance
Critical Repeat Outlet covers were not secured.
Do not operate the pool when the outlet covers are not secured. Secure the covers prior to the pool being placed back into operation. INSTALL MISSING SCREW IN DRAIN COVER. REPLACE FRAME IF NECESSARY.
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
Repeat The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request. KEEP RECORDS Correct By: 16-Feb-2022
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Total alkalinity was less than 60 ppm.
Raise the total alkalinity to at least 60 ppm. INCREASE ALKALINITY. Correct By: 16-Feb-2022
3701-31-04 (C)(8) / Spa water is drained at least every 30 days and is recorded
Spa water was not drained in the last 30 days.
Drain spa immediately and clean before placing the spa back in operation. COMPLETELY DRAIN SPA EVERY 30 DAYS. Correct By: 16-Feb-2022
3701-31-04(D)(6)(a)(1) / Combined chlorine shall not exceed 1.0 ppm.
Combined chlorine was greater than 1.0 ppm.
Treat the pool so that the combined chlorine is less than 1 ppm. DRAIN SPA AND REFILL OR SUPERCHLORINATE SPA. Correct By: 16-Feb-2022
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 09-February-2022