3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical The free chlorine level is less than the required 2.0 ppm.
THIS VIOLATION IS A IMMINENT HEALTH HAZARD AND THE SPA MUST CLOSE UNTIL THE FREE CHLORINE LEVEL IS 2.0 PPM OR MORE. Correct By: 08-Nov-2018
3701-31-04 ( D )(6)(a) / ORP reading shall be 650 millivolts or greater.
Repeat ORP reading was below 650 mv
Have the ACC unit inspected to determined why the ORP is low.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 08-November-2018