3701-31-04 (A) / All construction or alterations of a public swimming pool are approved
The disinfectant chemical feeder was replaced without approval.
SUBMIT AN EQUIPMENT REPLACEMENT NOTIFICATION TO THE OHIO DEPARTMENT OF HEALTH FOR THE REPLACEMENT OF THE DISINFECTANT CHEMICAL FEEDER. THE FLEXFLO PUMP WAS REPLACED WITH A STENNER PUMP
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request. KEEP DAILY OPERATIONAL RECORDS. THE SPA SHOULD NOT BE OPEN UNLESS DAILY RECORDS ARE KEPT.
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Total alkalinity was less than 60 ppm.
Raise the total alkalinity to at least 60 ppm.
3701-31-04(D)(6)(a)(1) / Combined chlorine shall not exceed 1.0 ppm.
Combined chlorine was greater than 1.0 ppm.
Treat the pool so that the combined chlorine is less than 1 ppm.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 01-March-2019