3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical No disinfection residual was present in the spa. DO NOT OPERATE SPA UNTIL DISINFECTION RESIDUAL IS >2.0 PPM.
It appears that the chemical feeder is not feeding. CHECK FEEDER.
3701-31-04 (B)(6)(h) / Required meters and gauges maintained/functional
FLOW METER was not functioning .
Maintain all meters and gauges in a properly funtioning manner at all times while the pool is in operation. REPAIR / REPLACE.
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Repeat Total alkalinity was at 30 ppm, less than 60 ppm. requirement.
Raise the total alkalinity to at least 60 ppm.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 23-August-2017