3701-31-04 (B)(6)(f) / Required turnover rates are sufficient
Repeat Required turnover rates were not met. Flow meter reading 160 gpm, required 208 minimum.
Have the circulation system evaluated to determine why the turnover rates are not able to be met. Once the reasons have been determined have the issue repaired. If necessary, submit plans to the Ohio Department of Health to review and approve.
3701-31-04 (C)(2) / pH is within 7.2 to 7.8
Corrected During Inspection pH was outside the range of 7.2 to 7.8. Reading was 8.0, corrected to 7.6
Treat the pool water so that the pH is within the acceptable range.
3701-31-04 (E)(2)(a)(i) / 12 ft. non-telescopic reach pole with shepherd's crook is provided
12 ft. non-telescopic reach pole with shepherd's crook was not visible.
Provide a 12 ft. non-telescopic reach pole in the pool area at all times.
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 27-June-2017