3701-31-04 (B)(1)(a) / Outlet covers shall be installed/secured/in compliance
Critical Repeat The equilizer outlet to the skimmer is not covered with a VGB cover.
PLUG THE EQUALIZER OUTLET AT THE WALL OR COVER THE OUTLET WITH A VGB COMPLIANT COVER.
3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical Repeat The free chlorine is less than the required 2 ppm.
This violation is a critical operational item and poses an imminent health hazard. THE SPA MUST BE CLOSED UNTIL THE VIOLATION IS CORRECTED AND THE HEALTH DEPARTMENT VERIFIES COMPLIANCE. Call the health department when the violation has been corrected at 440-219-7158.
3701-31-04 ( D )(6)(a) / ORP reading shall be 650 millivolts or greater.
Repeat ORP reading was below 650 mv
Have the ACC unit inspected to determined why the ORP is low.
3701-31-04 (A) / All construction or alterations of a public swimming pool are approved
Repeat The disinfectant chemicals feeder was replaced without submitting an ERN to the Ohio Department of Health.
SUBMIT AN EQUIPMENT REPLACEMENT NOTIFICATION TO THE OHIO DEPARTMENT OF HEALTH.
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
Repeat The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 10-April-2019