3701-31-04 (B)(6) / Equipment is maintained per manufacturers specifications.
Equipment was not maintained per manufacturers specifications. Records have not been kept since July 20 except once a week.
All equipment must be maintained in accordance with the manufacturers specifications. TEST AND RECORD THE CHLORINE LEVELS, pH, WATER TEMP WAS A DAY, ALKALINITY ONCE A WEEK, AND ACC AND SVRS ONCE A MONTH. Correct By: 28-Aug-2019
3701-31-04 (B)(6)(i) / A means of determining rate-of-flow on all water pumps
A means of determining rate-of-flow was not found for all water pumps. The jet pump on the spa does not have a flow meter or means of determining the flow rate.
Properly install a flow meter or have a pump curve available for every water pump used for the pool. INSTALL A MEANS OF DETERMINING THE FLOW RATE OF THE JET PUMP. Correct By: 28-Sep-2019
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 28-August-2019
|5.1(F)(2) Flow measuring devices. A means of determining rate-of-flow shall be properly installed and maintained on all public swimming pools, special features and jet pumps so that the rate of flow can be accurately determined and easily observed. One of the following methods to measure flow shall be used:|
(a) A flow meter; or
(b) A pump curve specific for the pump and impellor. The pump curve shall be conspicuously posted in the filter room and shall be marked up to display the formula or means for calculating the gauge readings into the total dynamic head (TDH) and the flow in gallons per minute (gpm).
A functional compound gauge shall be installed on the suction side of the pump, at or near the hair and lint strainer. A functional pressure gauge shall be installed on the pressure side of a pump, at or near the impellor housing;