3701-31-04 (B)(6)(y) / Chemicals are properly stored/used
Critical Chemical containers were stored without labels identifying the contents.
Label and properly store all chemical containers to avoid a chemical reaction or unnecessary exposure. LABEL THE CHLORINE CONTAINER. Correct By: 23-Feb-2023
3701-31-04 (D)(7) / Public spa shall have a functional automatic chemical controller
Critical The automatic chemical controller for the spa was not functioning properly. The flow switch/pump interlock was not functioning.
Have the ACC unit serviced or replaced if not able to be repaired. REPAIR ACC FLOW SWITCH. Correct By: 23-Feb-2023
3701-31-04 (B)(4)(c) / SVRS/APSOS/ACC test results/ service records are maintained
SVRS test results records were not maintained.
The test results/service records for these devices must be kept on site for review. TEST AND RECORD THE SVRS MONTHLY. RECORD ON THE WEEKLY LOG SHEETS. Correct By: 23-Feb-2023
3701-31-04 (C)(2) / pH is within 7.2 to 7.8
pH was outside the range of 7.2 to 7.8.
Treat the pool water so that the pH is within the acceptable range. ADJSUT pH. Correct By: 23-Feb-2023
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Repeat Total alkalinity was less than 60 ppm.
Raise the total alkalinity to at least 60 ppm. ADJUST ALKALINITY. 100 PPM IS IDEAL. Correct By: 23-Feb-2023
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 21-February-2023
|The Certificate of Compliance for the main drain covers is available in the equipment room. Our records show that the main drain suction outlet covers (Waterway 640-472xV) were installed 3/15/2021. The covers have a 7 year life span and must be replaced before 3/15/2028.|
The operator was observed performing onsite chemical tests appropriately and is aware of the acceptable parameters and necessary corrective actions.
Keep the chemicals’ Safety Data Sheets (SDS) in the equipment room and have Personal Protective Equipment (PPE) such as chemical gloves and goggles available for handling chemicals.