3701-31-04 (B)(6)(f) / Required turnover rates are sufficient
Repeat Required turnover rates were not met.
Have the circulation system evaluated to determine why the turnover rates are not able to be met. Once the reasons have been determined have the issue repaired. If necessary, submit plans to the Ohio Department of Health to review and approve. INCREASE FLOW RATE TO BETWEEN 208 AND 332 GPM
3701-31-04 (E)(4)(a) / Adequate number of lifeguards present for size of pool and bathers present
Critical Corrected During Inspection An adequate number of lifeguards were not present for size of pool and the number of bathers present. Lifeguards were not on duty during "ADULT SWIM"
Provide the proper number of lifeguards depending on the size of the pool and the number of bathers present at all times the pool is open for use. KEEP AT LEAST ONE LIFEGUARD ON DUTY DURING ADULT SWIM OR ANY TIME A BATHER IS IN THE WATER.
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 20-August-2019