3701-31-04 (B)(6)(f) / Required turnover rates are sufficient
Turnover rate was at 160 gpm. Required turnover rates (208 gpm) were not met.
Have the circulation system evaluated to determine why the turnover rates are not able to be met. Once the reasons have been determined have the issue repaired. If necessary, submit plans to the Ohio Department of Health to review and approve.
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 29-August-2016