3701-31-04 (A) / All construction or alterations of a public swimming pool are approved
Repeat ODH has not recorded receipt of ERN for the replacement of the disinfectant chemical pump.
SUBMIT ERN TO ODH FOR THE DISINFECTANT PUMP REPLACEMENT.
3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical Repeat The free chlorine reading was .4 ppm. At least 2.0 ppm is required.
The spa was open at the time of inspection. This violation is a critical operation item and poses an imminent health hazard. THE SPA MUST BE CLOSED UNTIL THE VIOLATION IS CORRECTED. CALL THE HEALTH DEPARTMENT 440-219-7158 BEFORE OPENING SO WE CAN VERIFY COMPLIANCE.
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
Repeat The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request.
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Total alkalinity was less than 60 ppm.
Raise the total alkalinity to at least 60 ppm.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 25-April-2019