3701-31-04 (B)(6)(f) / Required turnover rates are sufficient
Required turnover rates were not met.
Have the circulation system evaluated to determine why the turnover rates are not able to be met. Once the reasons have been determined have the issue repaired. If necessary, submit plans to the Ohio Department of Health to review and approve. INCREASE THE FLOW RATE TO BETWEEN 208 AND 332 GPM Correct By: 25-Jul-2019
3701-31-04 (B)(6)(s) / Perimeter barrier is in good repair to prevent unauthorized entry
Repeat There are still gaps between the bottom of the fence and the ground greater than 4 inches.
REDUCE THE GAPS UNDER THE FENCE TO LESS THAN 4 INCHES.
Facility Type: Pool
[?] Inspection Type: Standard
Inspection Date: 23-July-2019
|Corrections made since the 6-25-19 inspection|
-the skimmer equalizer outlets are plugged
-backflow preventers are on the hose bibs in the pump room
-the chlorine tank is labeled