3701-31-04 (B)(4)(a)(iv) / Water temperatures are recorded daily
Water temperatures were not being recorded daily.
Take and record the water temperature at least once/day. TEST WATER TEMPERATURE DAILY. Correct By: 05-Aug-2020
3701-31-04 (B)(4)(a)(vi) / Total alkalinity is tested weekly
Total alkalinity was not tested weekly.
Test total alkalinity at least once/week. TEST ALKALINITY WEEKLY. Correct By: 05-Aug-2020
3701-31-04 (C)(2) / pH is within 7.2 to 7.8
pH was outside the range of 7.2 to 7.8.
Treat the pool water so that the pH is within the acceptable range. ADJUST THE pH Correct By: 05-Aug-2020
3701-31-04 (D)(7)(e) / Automatic chemical controller shall be on the acceptable list maintained by the director.
Critical Automatic chemical controller in use was not on the acceptable list
Submit the ACC unit for placement on the acceptable list or replace the unit with a unit that is on the list. CONTACT THE OHIO DEPARTMENT OF HEALTH TO OBTAIN APPROVAL FOR THE AUTOMATIC CHEMICAL CONTROLLER UNIT THAT YOU HAVE ON THE SPRAY GROUNDS. 614-466-1390. Correct By: 03-Sep-2020
Facility Type: Special Use
[?] Inspection Type: Standard
Inspection Date: 03-August-2020
|Keep the chemicals’ Safety Data Sheets (MSDS) in the equipment room and have Personal Protective Equipment (PPE) such as chemical gloves and goggles available for handling chemicals.|
INSTALL A SELF-CLOSING GATE FOR THE POOL PER OAC 3701-31-04(B)(6)(s). SUBMIT PLANS TO THE OHIO DEPARTMENT OF HEALTH FOR APPROVAL.