3701-31-04 ( D )(6)(a) / ORP reading shall be 650 millivolts or greater.
ORP reading was below 650 mv
Have the ACC unit inspected to determined why the ORP is low.
3701-31-04 (A) / All construction or alterations of a public swimming pool are approved
Repeat The disinfectant chemical feeder was replaced without submitting an ERN to the Ohio Department of Health.
SUBMIT AN EQUIPMENT REPLACEMENT NOTIFICATION TO THE OHIO DEPARTMENT OF HEALTH.
3701-31-04 (B)(1)(a) / Outlet covers shall be installed/secured/in compliance
Critical The equalizer outlet is not plugged or covered with a VGB compliant cover.
PLUG THE EQUALIZER OUTLET AT THE SPA WALL OR PLACE A VGB COMPLIANT COVER OVER THE OPENING.
3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical The free chlorine level is 1.0 ppm. The required level is 2.0 ppm.
This violation is a critical operational item and poses an imminent health hazard. THE SPA MUST CLOSE UNTIL THE VIOLATION IS CORRECTED AND THE HEALTH DEPARTMENT VERIFIES COMPLIANCE. Call the health department when the violation has been corrected at 440-219-7158.
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
Repeat The licensee /authorized representative was not keeping or maintaining operational records.
All facility records must be maintained and available for review upon request. KEEP OPERATIONAL RECORDS. ACC AND SVRS FUNCTION NOT RECORDED.
3701-31-04(D)(6)(a)(2) / Pool free chlorine disinfectant residual shall be above 1 ppm.
Critical Pool free chlorine disinfectant residual was below 1 ppm.
Do not operate the pool until the chlorine disinfectant residual is at 1 ppm or above.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 08-April-2019
|A flow meter nor a pressure and vacuum gauge is not the spa jet pump for determining the flow rate of the jet pump.|