3701-31-04 (B)(1)(c) / Minimum disinfection residual shall be maintained as required.
Critical Repeat Corrected During Inspection Free Chlorine level was at 1.0 ppm.
Free Clorine level corrected and adjusted to 4.0 ppm.
3701-31-04 (B)(4) / The licensee /authorized representative is keeping records
The licensee /authorized representative was not keeping or maintaining operational records per rule. Based on hours of operation, two chemical readings must be taken and recorded.
Do two chemical readings and record per rule.
3701-31-04 (B)(4)(a)(vi) / Total alkalinity is tested weekly
Total alkalinity was not tested weekly and recorded on weekly operation report.
Test total alkalinity at least once/week and record.
3701-31-04 (B)(6)(i) / A means of determining rate-of-flow on all water pumps
Repeat A means of determining rate-of-flow was not found for all water pumps.
Properly install a flow meter or have a pump curve available for every water pump used for the pool.
3701-31-04 (C)(2) / pH is within 7.2 to 7.8
Repeat pH was outside the range of 7.2 to 7.8.
Treat the pool water so that the pH is within the acceptable range.
3701-31-04 (C)(3) / Total alkalinity is at or greater than 60 ppm
Repeat Total alkalinity was less than 60 ppm.
Raise the total alkalinity to at least 60 ppm.
Facility Type: Spa
[?] Inspection Type: Standard
Inspection Date: 14-November-2017